Please copy and paste this embed script to where you want to embed

Project

Subject

IOCL / BHEL PANIPAT

DESIGN CALCULATION

4xFr. – 6B GT COGEN PLANT

FOR

Doc. No.

Rev

4-38121-****

A

SOAK PIT

Sheet No. 1

TABLE OF CONTENTS

1.0.0PROBLEM STATEMENT.............................................................................................................2 2.0.0CONSIDERATIONS.......................................................................................................................2 3.0.0DESIGN DATA................................................................................................................................2 4.0.0DESIGN CRITERIA.......................................................................................................................2 5.0.0 CALCULATION.............................................................................................................................3 6.0.0SUMMARY......................................................................................................................................4

/var/www/apps/conversion/tmp/scratch_3/160221435.doc 23/12/03

Section

UR / EL

Project

Subject

IOCL / BHEL PANIPAT

DESIGN CALCULATION

4xFr. – 6B GT COGEN PLANT

FOR

Doc. No.

Rev

4-38121-****

A

SOAK PIT

1.0.0

1. To size 1 no. Soak pit for 4 nos. GTs of capacity 50 MVA each. 2. To size one no. Soak pit for 1 GT of capacity 50 MVA and 2 Power Transformers of capacity 31 MVA each.

2.0.0

To size one no. Soak pit for 2 Tie Transformers of capacity 37.5MVA each.

CONSIDERATIONS 3 nos. soak pits have been considered in the transformer yard. The capacity of each soak pit is calculated taking the largest transformer oil capacity.

3.0.0

DESIGN DATA Soak pit 1 (Located on the western side of s/s28 Building): Rating of Generator transformer is assumed as follows: •

Rating : 50 MVA

•

Oil capacity: 18000 litres….( As per BHEL Recommendation )

Soak pit 2 (Located on the Eastern side of s/s28 Building): Rating of Generator transformer is assumed as follows: •

Rating : 50 MVA

•

Oil capacity : 18000 litres….( As per BHEL Recommendation )

Rating of Power Transformer is assumed as follows: •

Rating : 31 MVA

•

Oil capacity: 12500 litres ….( As per BHEL Recommendation )

Soak pit 3 (to be located near the tie Tie Trafo yard suitably): Rating of Tie transformer is assumed as follows:

4.0.0

•

Rating : 37.5 MVA

•

Oil capacity : 29000 litres….( As per BHEL Recommendation )

DESIGN CRITERIA •

Soak pit volume shall be 125 % of the oil volume of the largest transformer.

/var/www/apps/conversion/tmp/scratch_3/160221435.doc 23/12/03

Sheet No. 2

PROBLEM STATEMENT

3.

Section

UR / EL

Project

Subject

IOCL / BHEL PANIPAT

DESIGN CALCULATION

4xFr. – 6B GT COGEN PLANT

FOR

Doc. No.

Rev

Section -

4-38121-****

A

Sheet No.

SOAK PIT

5.0.0

3

CALCULATION H1 1

Soak pit 1: Soak pit volume

= 1.25 * 18000

H2

= 22500 litres If the drain pipe (150-mm dia.) from the transformer’s individual oil pits are to be connected to the soak pit with a slope of 1 in 100. H1

= 0.15 + (1/100)*50, where 50 is the distance of soak pit from the transformer oil pit = 0.65 metre

For a volume of 22.5 cubic meter, assuming length as 4.5 m and breadth as 3.5 m H2

= 22.5/(4.5 *3.5) = 1.43 metre.

Total height of soak pit

= H 1 + H2 = 0.65 + 1.43 = 2.08 metre

Dimension of Soak pit 1 (L * B * H) is 4.5m * 3.5m * 2.08 m Soak pit 2: Soak pit volume

= 1.25 * 18000

H2

= 22500 litres If the drain pipe (150-mm dia.) from the transformer’s individual oil pits are to be connected to the soak pit with a slope of 1 in 100. H1

= 0.15 + (1/100)*50, where 50 is the distance of soak pit from the transformer oil pit

/var/www/apps/conversion/tmp/scratch_3/160221435.doc 23/12/03

UR / EL

Project

Subject

IOCL / BHEL PANIPAT

DESIGN CALCULATION

4xFr. – 6B GT COGEN PLANT

FOR

Doc. No.

Rev

4-38121-****

A

SOAK PIT

For a volume of 22.5 cubic meter, assuming length as 4.5 m and breadth as 3.5 m = 22.5/(4.5 *3.5) = 1.43 metre. Total height of soak pit

= H 1 + H2 = 0.65 + 1.43 = 2.08 metre

Dimension of Soak pit 1 (L * B * H) is 4.5m * 3.5m * 2.08 m

Soak pit 3: Soak pit volume

= 1.25 * 29000 = 36,250 litres

If the drain pipe (150-mm dia.) from the transformer’s individual oil pits are to be connected to the soak pit with a slope of 1 in 100. H1

= 0.15 + (1/100)*8, where 8 is the distance of soak pit from the transformer oil pit = 0.23 metre

For a volume of 36,250 cubic meter, assuming length as 5 m and breadth as 4.75 m H2

= 36.250/(5x4.75) = 1.53 metre.

Total height of soak pit

= H 1 + H2 = 0.23 + 1.53 = 1.76 metre

Dimension of Soak pit 2 (L * B * H) is 5m * 4.75m * 1.76m 6.0.0

SUMMARY Soak pit sizes are thus calculated.

/var/www/apps/conversion/tmp/scratch_3/160221435.doc 23/12/03

Sheet No. 4

= 0.65 metre

H2

Section

UR / EL

View more...
Subject

IOCL / BHEL PANIPAT

DESIGN CALCULATION

4xFr. – 6B GT COGEN PLANT

FOR

Doc. No.

Rev

4-38121-****

A

SOAK PIT

Sheet No. 1

TABLE OF CONTENTS

1.0.0PROBLEM STATEMENT.............................................................................................................2 2.0.0CONSIDERATIONS.......................................................................................................................2 3.0.0DESIGN DATA................................................................................................................................2 4.0.0DESIGN CRITERIA.......................................................................................................................2 5.0.0 CALCULATION.............................................................................................................................3 6.0.0SUMMARY......................................................................................................................................4

/var/www/apps/conversion/tmp/scratch_3/160221435.doc 23/12/03

Section

UR / EL

Project

Subject

IOCL / BHEL PANIPAT

DESIGN CALCULATION

4xFr. – 6B GT COGEN PLANT

FOR

Doc. No.

Rev

4-38121-****

A

SOAK PIT

1.0.0

1. To size 1 no. Soak pit for 4 nos. GTs of capacity 50 MVA each. 2. To size one no. Soak pit for 1 GT of capacity 50 MVA and 2 Power Transformers of capacity 31 MVA each.

2.0.0

To size one no. Soak pit for 2 Tie Transformers of capacity 37.5MVA each.

CONSIDERATIONS 3 nos. soak pits have been considered in the transformer yard. The capacity of each soak pit is calculated taking the largest transformer oil capacity.

3.0.0

DESIGN DATA Soak pit 1 (Located on the western side of s/s28 Building): Rating of Generator transformer is assumed as follows: •

Rating : 50 MVA

•

Oil capacity: 18000 litres….( As per BHEL Recommendation )

Soak pit 2 (Located on the Eastern side of s/s28 Building): Rating of Generator transformer is assumed as follows: •

Rating : 50 MVA

•

Oil capacity : 18000 litres….( As per BHEL Recommendation )

Rating of Power Transformer is assumed as follows: •

Rating : 31 MVA

•

Oil capacity: 12500 litres ….( As per BHEL Recommendation )

Soak pit 3 (to be located near the tie Tie Trafo yard suitably): Rating of Tie transformer is assumed as follows:

4.0.0

•

Rating : 37.5 MVA

•

Oil capacity : 29000 litres….( As per BHEL Recommendation )

DESIGN CRITERIA •

Soak pit volume shall be 125 % of the oil volume of the largest transformer.

/var/www/apps/conversion/tmp/scratch_3/160221435.doc 23/12/03

Sheet No. 2

PROBLEM STATEMENT

3.

Section

UR / EL

Project

Subject

IOCL / BHEL PANIPAT

DESIGN CALCULATION

4xFr. – 6B GT COGEN PLANT

FOR

Doc. No.

Rev

Section -

4-38121-****

A

Sheet No.

SOAK PIT

5.0.0

3

CALCULATION H1 1

Soak pit 1: Soak pit volume

= 1.25 * 18000

H2

= 22500 litres If the drain pipe (150-mm dia.) from the transformer’s individual oil pits are to be connected to the soak pit with a slope of 1 in 100. H1

= 0.15 + (1/100)*50, where 50 is the distance of soak pit from the transformer oil pit = 0.65 metre

For a volume of 22.5 cubic meter, assuming length as 4.5 m and breadth as 3.5 m H2

= 22.5/(4.5 *3.5) = 1.43 metre.

Total height of soak pit

= H 1 + H2 = 0.65 + 1.43 = 2.08 metre

Dimension of Soak pit 1 (L * B * H) is 4.5m * 3.5m * 2.08 m Soak pit 2: Soak pit volume

= 1.25 * 18000

H2

= 22500 litres If the drain pipe (150-mm dia.) from the transformer’s individual oil pits are to be connected to the soak pit with a slope of 1 in 100. H1

= 0.15 + (1/100)*50, where 50 is the distance of soak pit from the transformer oil pit

/var/www/apps/conversion/tmp/scratch_3/160221435.doc 23/12/03

UR / EL

Project

Subject

IOCL / BHEL PANIPAT

DESIGN CALCULATION

4xFr. – 6B GT COGEN PLANT

FOR

Doc. No.

Rev

4-38121-****

A

SOAK PIT

For a volume of 22.5 cubic meter, assuming length as 4.5 m and breadth as 3.5 m = 22.5/(4.5 *3.5) = 1.43 metre. Total height of soak pit

= H 1 + H2 = 0.65 + 1.43 = 2.08 metre

Dimension of Soak pit 1 (L * B * H) is 4.5m * 3.5m * 2.08 m

Soak pit 3: Soak pit volume

= 1.25 * 29000 = 36,250 litres

If the drain pipe (150-mm dia.) from the transformer’s individual oil pits are to be connected to the soak pit with a slope of 1 in 100. H1

= 0.15 + (1/100)*8, where 8 is the distance of soak pit from the transformer oil pit = 0.23 metre

For a volume of 36,250 cubic meter, assuming length as 5 m and breadth as 4.75 m H2

= 36.250/(5x4.75) = 1.53 metre.

Total height of soak pit

= H 1 + H2 = 0.23 + 1.53 = 1.76 metre

Dimension of Soak pit 2 (L * B * H) is 5m * 4.75m * 1.76m 6.0.0

SUMMARY Soak pit sizes are thus calculated.

/var/www/apps/conversion/tmp/scratch_3/160221435.doc 23/12/03

Sheet No. 4

= 0.65 metre

H2

Section

UR / EL

Thank you for interesting in our services. We are a non-profit group that run this website to share documents. We need your help to maintenance this website.

To keep our site running, we need your help to cover our server cost (about $400/m), a small donation will help us a lot.